Firm frequency response (FFR)
FFR creates a route to market for providers whose services may otherwise be inaccessible. The FFR service gives us and service providers both a degree of stability against price uncertainty under the mandatory service arrangements.
The current Testing Guidance Document can be found here. We have published the Draft FFR Testing Guidance Document currently open for consultation and the Covering Letter. This is an opportunity for the industry to feedback on the proposed changes. The deadline for responses to the proposed changes is 5pm on the 7th September 2018.
Update to the Outline Change Proposal (OCP) for Firm Frequency Response (FFR): We are considering the extensive number of responses and comments received. We will confirm and make available our final conclusions no later than the 7th September 2018. We have published the Outline Change Proposal (OCP) for Firm Frequency Response (FFR). This is an opportunity for the industry to feedback on the proposed changes to the service. Part of this OCP is the simplification of the Standard Contract Terms (SCT) as stated in the product road map for frequency response and reserve. Please use this link for the draft version of the simplified SCTs included in this OCP. The deadline for responses is 5pm on the 12th July 2018
FFR can provide both dynamic and non-dynamic response to changes in frequency:
Dynamic frequency response is a continuously provided service used to manage the normal second-by-second changes on the system.
Non-dynamic frequency response is typically a discrete service triggered at a defined frequency deviation.
There are three response speeds for frequency response.
Providers may offer only one of these or a combination of different response times.
Primary response - Response provided within 10 seconds of an event, which can be sustained for a further 20 seconds.
Secondary response - Response provided within 30 seconds of an event, which can be sustained for a further 30 minutes.
High frequency response - Response provided within 10 seconds of an event, which can be sustained indefinitely.
The FFR service is open to both Balancing Mechanism (BM) and non-BM providers who can meet the technical requirements. This might include generators connected to the transmission and distribution networks, storage providers and aggregated demand side response.
Providers can offer other balancing services outside of their tendered FFR windows.
Units must be ready and in frequency sensitive mode at the start of each FFR window.